Effective August 1, 2015
Addendum: Addition of new/revised requirements not identified in the original SUN issued August 30, 2013
Effective Date (see Schedule below): August 1, 2015
Impact Statement: A review of all Listing Reports is necessary to determine which products comply with new/revised requirements and which products will require re-evaluation. NOTE: Effective immediately, this revised standard will be exclusively used for evaluation of new products unless the Applicant requests in writing that current requirements be used along with their understanding that their listings will be withdrawn on Effective Date noted above, unless the product is found to comply with new/revised requirements.
Overview of Changes: Addition of testing and marking requirements. Specific details of new/revised requirements are found in table below.
Schedule: So that shipping of products with Listing Marks will not be interrupted, an approximate schedule has been established to ensure Listing Reports are found compliant by Effective Date:
Fees: An initial review of Listing Report (s) will be covered by a direct billing project and will be invoiced at not more than $1000 per report.
Client Action Required:
Information – To assist our Engineer with review of your Listing Reports, please submit technical information in response to the new/revised paragraphs noted in the attached or explain why these new/revised requirements do not apply to your product (s).
Current Listings Not Active? – Please immediately identify any current Listing Reports or products that are no longer active and should be removed from our records. We will do this at no charge as long as Intertek is notified in writing prior to the review of your reports.
NOTE: Additions to existing requirements are underlined and deletions are shown
lined out below.
|NEW ADDENDUM SUN REQUIREMENTS|
|7.17.2||Addition of deflection range marking requirements for expansion-deflection or deflection fittings.|
|7.18.2||New marking requirement for a FITTING for metal-clad cable, Type ACG90 and Type ACGWU90 cable as described in Clause 184.108.40.206, the carton shall be marked "Armored CableBUSHING Required on _____" or equivalent wording. The blank shall be filled in with "Metal-Clad Cable" or "Type ACG90 Cable" or "Type ACGWU90 Cable".|
Note: See Annex C for guidance on armored cable bushing size.
|220.127.116.11-5||New Deflection Test method for EXPANSION-DEFLECTION or DEFLECTION FITTINGS|
|EXISTING SUN INFORMATION NOTED BELOW|
|This grouping of new/revised paragraphs were from revisions to standard dated November 6, 2009|
|18.104.22.168, 22.214.171.124A, 7.20.1, 7.20.2, 8.5A||Revision of Clause 126.96.36.199 and addition of new Clauses 7.20.1, 7.20.2 and 8.5A to provide construction, marking, and performance requirements needed to evaluate fittings with alternative corrosion protection|
|6.2.3, 188.8.131.52, 184.108.40.206||Revision to Clauses 6.2.3, 220.127.116.11, and 18.104.22.168 to clarify test requirements and add marking requirements specific to Type ACG90 and Type ACGWU90.|
|This grouping of new/revised paragraphs were from revisions to standard dated July 13, 2012|
|3.29, 22.214.171.124, 126.96.36.199, 7.18, 7.18.2||Transition couplings are intended for connection of one or more metal sheathed cables or flexible metal conduits to one or more non-flexible metallic raceways. Requirements for couplings are detailed in UL Standard for Conduit, Tubing, and Cable Fittings, UL 514B, and compliance needs to be confirmed and reports updated.|
|6.1.3||A fitting for cable must have an end stop or throat of an appropriate size to allow passage of cable conductors. The conductors of the largest and smallest cable size will be evaluated. This revision is to address concerns expressed that the conductors of the cable will not fit through the fitting end stop or throat when assembled in the field|
|6.3.1||Transition couplings are intended for connection of one or more metal sheathed cables or flexible metal conduits to one or more non-flexible metallic raceways. Requirements for couplings are detailed in the UL Standard for Conduit, Tubing, and Cable Fittings, UL 514B, and compliance needs to be confirmed and reports updated.|
CUSTOMERS PLEASE NOTE: This Table and column "Verdict" can be used in determining how your current or future production is or will be in compliance with new/revised requirements.