Effective December 9, 2016
Effective Date (see Schedule below): December 9, 2016
Impact Statement: A review of all Listing Reports is necessary to determine which products comply with new/revised requirements and which products will require re-evaluation. NOTE: Effective immediately, this revised standard will be exclusively used for evaluation of new products unless the Applicant requests in writing that current requirements be used along with their understanding that their listings will be withdrawn on Effective Date noted above, unless the product is found to comply with new/revised requirements.
Overview of Changes (Specific details of new/revised requirements are found in table below):
If the applicable requirements noted in the table are not described in your report(s), these requirements will need to be confirmed as met and added to your report(s) such as markings, instructions, test results, etc. (as required).
Schedule: So that production of products bearing Listing Marks will not be interrupted, the following schedule of approximate dates has been established to ensure Listing Reports are found compliant by Effective Date:
Fees: An initial review of Listing Report (s) will be covered by a direct billing project and will be invoiced at not more than $1000 per report.
Client Action Required:
Information – To assist our Engineer with review of your Listing Reports, please submit technical information in response to the new/revised paragraphs noted in the attached or explain why these new/revised requirements do not apply to your product (s).
Current Listings Not Active? – Please immediately identify any current Listing Reports or products that are no longer active and should be removed from our records. We will do this at no charge as long as Intertek is notified in writing prior to the review of your reports.
|15||Information on or in the Cable|
Additions to existing requirements are underlined below.
The following information shall appear at the intervals indicated in 13.1 throughout the entire length of the finished cable. Except for (a), the sequence of items is not specified. Other information, where added, shall not confuse or mislead and shall not conflict with these requirements. See 18.1 for date marking.
a) CABLE TYPE-LETTER DESIGNATION – Use of the word ²Type² is not required:
²Type OFNP² and ²Type OFCP² for cables that comply with the requirements in this
²Type OFNR² and ²Type OFCR² for cables that comply with the requirements in this
²Type OFNG² and ²Type OFCG² for cables that comply with the requirements in this
²Type OFN² and ²Type OFC² for cables that comply with the requirements in this
b) RESPONSIBLE ORGANIZATION – The name of the cable manufacturer, that manufacturer’s trade name for the cable, or both, or any other appropriate distinctive marking by means of which the organization responsible for the cable is readily identifiable. Where the organization responsible for the cable is different from the actual manufacturer, both the responsible organization and the actual manufacturer shall be identified by name or by appropriate coding such as trade name, trademark, or the assigned electrical reference number. It is appropriate to identify the actual manufacturer by the assigned colored marker thread or combination of colored marker threads; however, unless it or they supplement ink printing as stated in 15.3 and 15.4, colored marker thread(s) shall not be used to identify the responsible organization. The meaning of any coded identification shall be made available by the organization responsible for the cable. It is appropriate also to identify a private labeler; the means is not specified. See 15.2 and 15.4.
c) The designation ²Limited Combustible² for Type OFNP or OFCP plenum cable that complies with the requirements in 12.1. This marking is not required.
d) The designation ²sun res² or ²sunlight resistant² for cable that complies with the sunlight resistance test referenced in 10.1.
e) For cables rated over 60°C, the temperature rating shall be stated as °C or C.
f) For OFN, OFC, OFNG and OFCG cables, the designation ²-LS² (signifying ²limited smoke²) for cables that comply with the fire and smoke requirements in the Standard for Vertical-Tray Fire-Propagation and Smoke-Release Test for Electrical and Optical-Fiber Cables, UL 1685. This marking is not required.
CUSTOMERS PLEASE NOTE: This Table and column "Verdict" can be used in determining how your current or future production is or will be in compliance with new/revised requirements.