Enabling you to identify and mitigate the intrinsic risk in your operations, supply chains and business processes.
Evaluating how your products and services meet and exceed quality, safety, sustainability and performance standards.
Validating the specifications, value and safety of your raw materials, products and assets.
Effective June 22, 2017
Effective Date (see Schedule below): June 22, 2017
Impact Statement: A review of all Listing Reports is necessary to determine which products comply with new/revised requirements and which products will require re-evaluation. NOTE: Effective immediately, this revised standard will be exclusively used for evaluation of new products unless the Applicant requests in writing that current requirements be used along with their understanding that their listings will be withdrawn on Effective Date noted above, unless the product is found to comply with new/revised requirements.
Overview of Changes (Specific details of new/revised requirements are found in table below):
If the applicable requirements noted in the table are not described in your report(s), these requirements will need to be confirmed as met and added to your report(s) such as markings, instructions, test results, etc. (as required).
Schedule: So that shipping of products with Listing Marks will not be interrupted, an approximate schedule has been established to ensure Listing Reports are found compliant by Effective Date:
Fees: An initial review of Listing Report (s) will be covered by a direct billing project and will be invoiced at not more than $1000 per report.
Client Action Required:
Information – To assist our Engineer with review of your Listing Reports, please submit technical information in response to the new/revised paragraphs noted in the attached or explain why these new/revised requirements do not apply to your product (s).
Current Listings Not Active? – Please immediately identify any current Listing Reports or products that are no longer active and should be removed from our records. We will do this at no charge as long as Intertek is notified in writing prior to the review of your reports.
|1.1||Additions to existing requirements are underlined and deletions are shown |
This Standard applies to form wound rotating electrical machines rated less than 460 volts and all other rotating electrical machines and linear motors, both AC and DC, rated
|10.6.1||New clause added;|
A generator shall provide in a location inaccessible from outside the assembly in its end use application:
a) A flat, unpainted, corrosion protected, surface integral with or irreversibly connected to the generator barrel that is properly sized for the generator’s fault current capability; and
b) Tapped with a hole or holes for machine thread fasteners or other approved method for securing any grounding conductor(s) for equipment provided with the generator and grounding conductor terminals properly sized for the generator’s fault current capability.
Exception: The generator foot or mounting location shall not be prohibited as a secondary location when all criteria in (a) are satisfied elsewhere on the generator.
|Table 18.2 & Table 18.4||Tables 18.2-Minimum acceptable spacings at field wiring terminals for voltages over 750 V & Table 18.4 - Minimum acceptable spacings at other than field-wiring terminals – have been revised to remove all voltage rating above 1000 Volts per the scope change referenced above|
CUSTOMERS PLEASE NOTE: This Table and column "Verdict" can be used in determining how your current or future production is or will be in compliance with new/revised requirements.