Effective January 1, 2017
Effective Date (see Schedule below): January 1, 2017
Impact Statement: A review of all Listing Reports is necessary to determine which products comply with new/revised requirements and which products will require re-evaluation. NOTE: Effective immediately, this revised standard will be exclusively used for evaluation of new products unless the Applicant requests in writing that current requirements be used along with their understanding that their listings will be withdrawn on Effective Date noted above, unless the product is found to comply with new/revised requirements.
Overview of Changes: This revision is being issued to include new construction requirements for components intended for use with carbon dioxide and pressure test requirement for tubing. Specific details of new/revised requirements are found in table below.
If the applicable requirements noted in the table are not described in your report(s), these requirements will need to be confirmed as met and added to your report(s) such as markings, instructions, test results, etc. (as required).
Schedule: So that shipping of products with Listing Marks will not be interrupted, an approximate schedule has been established to ensure Listing Reports are found compliant by Effective Date:
Fees: An initial review of Listing Report (s) will be covered by a direct billing project and will be invoiced at not more than $1000 per report.
Client Action Required:
Information – To assist our Engineer with review of your Listing Reports, please submit technical information in response to the new/revised paragraphs noted in the attached or explain why these new/revised requirements do not apply to your product (s).
Current Listings Not Active? – Please immediately identify any current Listing Reports or products that are no longer active and should be removed from our records. We will do this at no charge as long as Intertek is notified in writing prior to the review of your reports.
|5.6.3||New clause added;|
A component intended for use with carbon dioxide (R744) as a refrigerant, meeting the requirements of Clause 22.214.171.124(c) shall be protected by a pressure relief device or fusible plug or shall have provision (e.g., a fitting) for the installation of a pressure relief device or fusible plug.
|Additions to existing requirements are underlined and deletions are shown |
Refrigerant-containing components or parts shall be constructed to withstand the following:
a) for high-side parts, a pressure equal to the greater of
ii) five times the minimum high-side design pressure specified in CSA B52;
ii) three times the minimum low-side design pressure specified in CSA B52; or
iii) three times the vapour pressure of the refrigerant at 27 °C (80.6°F).
|6.1.5||Clause has been deleted;|
Components made from continuous tubing or lengths of tubing having telescoped joints shall be considered acceptable without testing if the tubing meets the requirements of Clause 5.4.1.
CUSTOMERS PLEASE NOTE: This Table and column "Verdict" can be used in determining how your current or future production is or will be in compliance with new/revised requirements.