Effective November 6, 2015
Effective Date (see Schedule below): November 6, 2015
Impact Statement: A review of all Listing Reports is necessary to determine which products comply with new/revised requirements and which products will require re-evaluation. NOTE: Effective immediately, this revised standard will be exclusively used for evaluation of new products unless the Applicant requests in writing that current requirements be used along with their understanding that their listings will be withdrawn on Effective Date noted above, unless the product is found to comply with new/revised requirements.
Overview of Changes: The August 26, 2014 update includes revised requirements for automatic safety shutoff valves and gas flow controls. The October 29, 2014 update includes revised requirements of the accelerated aging test evaluation requirement for gaskets made of neoprene or rubber compound. Specific details of new/revised requirements are found in table below.
Schedule: So that shipping of products with Listing Marks will not be interrupted, an approximate schedule has been established to ensure Listing Reports are found compliant by Effective Date:
Fees: An initial review of Listing Report (s) will be covered by a direct billing project and will be invoiced at not more than $1000 per report.
Client Action Required:
Information – To assist our Engineer with review of your Listing Reports, please submit technical information in response to the new/revised paragraphs noted in the attached or explain why these new/revised requirements do not apply to your product(s).
Current Listings Not Active? – Please immediately identify any current Listing Reports or products that are no longer active and should be removed from our records. We will do this at no charge as long as Intertek is notified in writing prior to the review of your reports.
NOTE: Additions to existing requirements are underlined and deletions are shown
lined out below.
New/Revised Requirements from Revision August 26, 2014;
Revised requirements for automatic safety shutoff valves and gas flow controls.
|41.3.2||Info||Gas Flow Controls|
|184.108.40.206||Info||Automatic valves and automatic safety shutoff valves (ASSV)|
Automatic safety shutoff valve (ASSV):
Automatic valves and automatic safety shutoff valves shall comply with the applicable requirements in the Standard for Automatic Valves for Gas Appliances, ANSI Z21.21, including the following:
New/Revised Requirements from Revision October 29, 2014;
Revise the accelerated aging test evaluation requirement for gaskets made of neoprene or rubber compound.
|72.1||The enclosure of an outdoor unit shall be protected against outdoor exposure in accordance with the requirements in 72.2 – |
Gaskets depended upon for protection from rain shall be made of neoprene, rubber compounds or solid polyvinyl-chloride materials, except foamed materials, and shall:
In accordance with the requirements in 72.15, gaskets depended upon for protection from rain and made of neoprene, or rubber compounds
Exception: The test is not required when the gaskets comply with the requirements in the Standard for Gaskets and Seals, UL 157.
|Table 73.1||Physical properties for gaskets|
CUSTOMERS PLEASE NOTE: This Table and column "Verdict" can be used in determining how your current or future production is or will be in compliance with new/revised requirements.